Not sensing any heat and receiving error code 228 from your Lennox® furnace?
This indicates your HVAC equipment couldn’t adjust its pressure switch before starting. As a consequence, your system will not run for your protection.
Repairing or replacing this part is better left to the professionals at Golden Seal Service Experts Heating & Air Conditioning in Saint Charles. Our NATE-certified technicians are among the elite in the industry. They’re well-equipped to work on all of your heating needs, including clearing a furnace error.
We want you to be thoroughly satisfied with our quality furnace repair in Saint Charles. That’s why we back it with a 100% Satisfaction Guarantee* for a year.
How a Pressure Switch Works
This part plays a prominent part as your furnace prepares to warm your space.
Here’s what occurs after your thermostat’s call for heat:
- Your furnace’s control board starts running the draft inducer blower motor. This drains combustion gases from the heat exchanger and moves in new gas and air so the burners can fire.
- When the pressure switch senses that enough air is being pulled into the burners, it closes and commands the control board to ignite the furnace.
- Your furnace ignites and supplies heat.
What Happens When a Pressure Switch Fails
When your pressure switch isn’t functioning promptly, you’ll likely hear the fan start and the switch clicking multiple times before the furnace turns off completely. When a part isn’t working right, your furnace will turn off for your safety.
Your furnace will tell you something is amiss with a red flash from its indicator light, which it uses to exhibit error codes. It uses this red light to flash code, like Morse code.
You may see quick flashes or an alternating slow flash as it passes on a fault code.
Estimated Repair Cost for Furnace Error Code 228
Before replacing the switch, your Golden Seal Service Experts Heating & Air Conditioning Expert will look at other parts of your furnace first. Several other issues can also cause the error code, like a blocked vent or cracked hose.
The bill to fix your furnace depends on what’s wrong with it and how long it takes to fix it.
If your pressure switch needs to be replaced, you can expect to pay between $40 to $350.
Count on the Experts at Golden Seal Service Experts Heating & Air Conditioning
If you require furnace repair, reach out to the professionals from Golden Seal Service Experts Heating & Air Conditioning to diagnose the fault code and fix the problem to your standards.
Call us at 630-246-2698 or schedule an appointment online today.